Please use this identifier to cite or link to this item:
|Title:||The cogeneration steam turbine of the tp-35/40-8.8 type|
|Authors:||Valamin, A. Y.|
Kultyshev, A. Y.
Goldberg, A. A.
Sakhnin, Y. A.
Shekhter, M. V.
Aguilera, H. C. Paneque
Stepanov, M. Y.
Shibaev, T. L.
|Citation:||The cogeneration steam turbine of the tp-35/40-8.8 type / A. Y. Valamin, A. Y. Kultyshev, A. A. Goldberg, Y. A. Sakhnin, M. V. Shekhter, H. C. Paneque Aguilera, M. Y. Stepanov, T. L. Shibaev // Thermal Engineering. — 2012. — Vol. 59. — № 12. — P. 900-906.|
|Abstract:||The main performance characteristics of the turbine, descriptions of the electrohydraulic control and protection system (EHCPS), the heat flow diagram, arrangement decisions, and motivation for selecting them, are given. The steam turbine presented by the Ural Turbine Works (UTW) is intended for replacing the VPT-25 turbine the service life of which has already expired at the Novokuybyshevsk CHP plant. The mixed- pressure turbine will operate in combination of the double-circuit heat recovery boiler (HRB) in a parallel scheme. High-pressure (HP) steam will be supplied from the main steam header to which high-pressure steam from the power boilers and the HRB will be fed, while low-pressure (LP) steam will be supplied directly from the HRB. For the turbine, nozzle steam distribution and the two-row control stage are adopted. The tur- bine has a process steam extraction line with its stop and control valve and heating steam extraction line lead- ing to the main steam collector. © Pleiades Publishing, Inc., 2012.|
|Appears in Collections:||Научные публикации, проиндексированные в SCOPUS и WoS CC|
Files in This Item:
|10.1134S0040601512120117_2012.pdf||622,76 kB||Adobe PDF||View/Open|
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.